Folks AC went down on RV.
Two units identical problem on both; Run and cool for about 15 minutes, kick off.
On arrival found hot compressor, checked thermal OL on compressor and verified closed. only two safeties, this one and freeze stat. no HPCO or LPCO.
Board is open, on an NO relay (both units). Jumped relaly and compr. ran. Cond. fan is running already indicating a call. Data phone cable type stat.; unable to check input. I suspect something in board/stat are holding unit out on temp; not able to find any trouble shooting for board/ or stat on Google, only find install instructions.
Unable to check charge, no access ports and don't have a piercing valve.
I cleaned both condensers but suspect this is not the problem. No oil noted around compressor or condenser indicating a leak
Why would the board hold out the compressor? What is it sensing? Time?
If let sit, several hours, the units will come back on again. I can't get past why the board and not the compr. thermal OL is tripping??!!??!!
Thank you, Clay