My folks have a home new to them that is having humidity problems. Running around 60%.. Long standing lung problems etc.. already in play, I need to get the humidity down.
It seems easy enough to drop the fan speed on cool down to medium, but I don't want to do something that will create a pressure problem and/or slug the compressor.
Still, I sorta think the expansion valve will handle that concern and I'll get just what I want: increased latent cooling, decreased sensible...
Fan speeds (short of a static test) are:
Hi = 1135 cfm
M = 960 cfm
L = 790
Heats on the low, cool is on the high. I'm thinking I move to cool, and the reduction seems in line with what I want, but...
Am I thinking wrong here?
And, does anybody have a manal for one of these?
Thanks guys! dan