I have an electrician who has installed the circuit feeding my 15 ton package unit. The unit's label say a max of 50 amps. He installed 60 amp breakers. I told him the label applied and that he needed to change them to 50 amp. He won't budge, he is claiming an allowance in the NEC section 440.22. which one applies?