Do I need zoning?
I have a two level 2100sq ft house. The problem I have is the upper floor is usually 10 degrees warmer then the lower level. When it is 95 outside, if I have the stat set to 73, it will be at least 85 upstairs. If I want it to be 75 on the upper floor on a warm night, I have to crank the AC down to 65.
All of the vents are currently 100% open. Is it normal to expect a 10 degree difference between the upper and lower levels? Does the house just need to be balanced, or, does it sound like there might be some other problem?
I have been thinking of zoning, but, want to make sure there is not something else going on first.
Any returns on the upper floor.
Are all the ducts/supples accessible.
You might try balancing first. It cost less, and may get results good enough that you don't need to zone.
Originally Posted by The_Pickle
My similar problem was solved by a combination of sealing massive basement leaks in my return system (the air was taking the path of least resitance)...and by insulating my attic with R-30 batts.
In the land of the blind.....the man with one eye is king....
There is a return of both floors. Although it seems like there is much less draw on the upper floor return. All the duct work on the upper floor is in the attic, lower level is in the crawl space. All accessible. It does seem as if the draw on the upper return is much less. Hard to tell though as I have no special tooling.
Originally Posted by beenthere
Your system is easy to zone then.
Your second floor return is probably undersized, and that can hurt a lot. When trying ot cool it.