Yes, I had seen things online about multizone minisplits.
Originally Posted by Caveman1234
Could such a thing have the wall mount units on two different floors?
When you say it's ductless, does that mean it's transporting cold refrigerant in insulated lines to the various wall mount units?
Does the dehumidifying mode keep on removing humidity regardless of the temperature? I know it has a temperature below which it would ice up. But I mean, other than that.
Multiple floors OK
The indoor units do not have to be on the same floor. The Fuji spec allows for a difference of up to 49 feet between the units and a 66 foot limitation on the length of the lineset (pipes between the indoor and outdoor units). I have no idea what the effect on the performance and efficiency is when approaching (or exceeding) these limits.