Goodman 13 Seer Heat Pump
This was Posted Earlier but was moved
New Install--Outside unit and AHU--Heat Pump
10 Degree Slit on Air Temp inside-Ret and Supply
Superheat 10 Degrees--Tried Adjusting Charge--Superheat stayed 10 either way
Unit not Cooling Properly--Need 15-18 Degrees across Evap Coil.
R-22 System--Piston Metering Device.
It was moved to pro forum. You have replies there.
Read site rules. Since we aren't allowed to give DIY instruction in this forum.
We can't give technical advice to a pro in this forum either.
Goodman 13 Seer Not Cooling
The Unit has been Repaired--Due to a Leak on Installation--Too much Refrigerant was added back--Weighed in Charge and Now--15 Degree Superheat and 15 Degrees across Coil--10 Degree Subcooling--Thanks For all your Help!!!
Last edited by hvactech80; 07-27-2008 at 04:47 PM.