I am trying to start up a 20-ton straight cool condenser sitting on the ground. The heat exchanger is 3 stories up (125 ft line set and 5/8 liquid line). The unit has thermostatic expansion valve. The liquid line at the condenser is 255 psi and the liquid line at the heat exchanger is 205 psi. What could be causing the pressure loss? There is no filter.