The condenser coils look to be plugged up with lint. Best I can tell from
if you guys are looking at the pic of his gauges, you are looking at the register grill on the mech room door What was temp reading on the suction line, looks like an overcharge to me. did you hit em with water to see what the head did? Is the condenser fan spinning the right direction, fan blade set at the right height?
There are 4 commercial dryers venting there all the time. Vent temp is about 400*. I burnt myself on the liquid line - 140*. They wouldn't let me have access to the indoor coil and filter. But it's probably not exactly clean.
With a 450 lb head and that temp line. Hitthose coils with cleaner and watch the junk pour out. They are plugged with lint. (prob othe company rinseing with water only year after year)
The first man gets the pearl, All the second gets is the shell