Trane BCI-I comm and set up issue
Ran into a problem we get once in awhile with Intellipaks and JCI BMS
Basically, the Intellipaks are stuck in master/slave configuration and wont go into Standalone.
We have tried to unhitch (stop writing to) AO39 wich seems to be a pain in the A these past few months, but no luck.
I'm gonna log onto comfortsite tomorrow and see if I can find a points list newer than '09.
Anyone know how to pull the equipment out of master/slave config and move to standalone.
This gives me issues like no economizer, one unit is forced 100% ex, driving building static negative. Its some sort of comm or point issue with the bacnet card.
I have already reset all the bacnet cards and used the Trane bacnet sup-up tool, so I don't think doing that a 3rd time will help.