Pics of install - let the comments fly
Okay, here are some pics of the new equipment and a few of the old also. Please post your comments, questions and criticisms. Let me know if any specific or close up shops are needed and I'll try to post.
Trane XR14 HP w/ 90% XT furnace.
Old outside. I think I had a good 5 years left in this unit.
A few shots of the new inside equipment.
A few of the outside unit.
That little copper tube coming out the bottom there is the condensate drain.
looks good. where does the air filter go?
It's pretty but looking I see the condenser is sitting directly in front of the disconnect and that's a no-no. And I just don't like the A/C condensate and the furnace condensate tied into the same line where backflow can be possible. It's pretty though and I like the furnace and condenser pad install.
"The American Republic will endure until the day Congress discovers it can bribe the public with the public's own money.
- Alexis de Toqueville, 1835
Is that "yowza" in a good or bad way?
Originally Posted by DPSwitch
Is there a reason the disconnect shouldn't be directly behind the unit?
Originally Posted by DeltaT
My concern about the drain line was that it empties right at the foundation of the house and also right at the pad.
Thanks for the complement on the pad. I actually did most of that the day before they came. The old unit had sunk down some, so I needed to get it raised up some. I laid 3 sides and left them room to remove the old unit. Then finished it up while they were doing some inside work.
I also noticed they used electrical tape to wrap the pipes outside. I assume there was a better way to do that. That tape won't last long outside.
The gas line needs better support.
The Yowza was for the old stuff.
It was a good investment.
How come the combustion air intake doesn't terminate outside?
economic collapse is a certainty. debt based fiat currency monetary systems can never continue indefinitely because they require continuous creation of new debt to service the existing debt. in the absence of economical growth (which is always predicated on increased resource extraction rather than capital alone), this leads to massive inflation which destroys the currency.
your leaders can't fix this - they're corrupt and only exist to enrich themselves and their corporate friends.
Is the pipe in this photo for the furnace exhaust?
Sometimes installers use electrical tape outside when zip ties would be better. You could always get some black zip ties at a hardware store down the road if the electrical tape goes bad.
All things considered, I think it looks pretty good for the most part... There's a difference between looks and performance, as well as code.
indoor air for combustion...
whats going to keep the drain pipe from freezing in the winter??????
never ever use copper for the drain on a 90% furnace, the condensate will eat it up...
there was plenty of room to get that other filter case in there if they had used beenthere's design for the return box.....
Originally Posted by acobra289
violates electrical code and will not pass inspection around here.
did they get permits??
Yeah disconnect behind unit, not code.
need to be able to access it without coming into possible contact with unit.
Is that a dryer vent exit in the window to the left of the unit
oh yea, nice pad work there
Is that a dryer vent poking through the window to the left of the condensing unit? If so, not a good combination to have a dryer vent and an air breathing condensing unit nearby. Especially since that Trane has spine fin coils, which attract dirt like a magnet. Great heat transfer when they're clean, but not so hot when it's dirty.
At a minimum those coils should be cleaned yearly. WIth a dryer vent nearby, make that more often.