Well, at 109* OD temp, with that low vapor pressure and Sh.
A guess would be, a restriction at the LLFD if its external to the condenser.
Or, a restricted or dirty indoor pistion,
You can refresh my memory.
Did it ever cool right.
Results 14 to 26 of 47
Thread: Service Tech's numbers...
Used Equipment - Buy, Sell, Save!