Which Coil for this equipment?
Can someone tell me what is the right Lennox coil for this equipment (or if there is more than one which will work, which one is better and why)? Also, is there any specfic air filter you would recommend. Thank you.
Lennox XC15-036 3 ton 15 SEER A/C
Lennox G61MPV-90 90,000 BTU 94% effieicnt gas furnace with variable speed blower
Lennox XC15-030 2-1/2 ton 15 SEER A/C
Lennox G60UHV-070 70,000 BTU 80% efficient gas furnace with variable speed blower
Have the contractor that you choose provide you with the correct ARI certificate number.
Originally Posted by JJMJD
There are most likely multiple choices for your equipment, and since you have variable speed equipment all three items must be matched.
I would look it up but I have 10,000 things to do right now.
C33-43 with a G61MPV-36C-090 is rated at 15.20 SEER Cert # 1329808
C33-31 with a G60UHV-36B-070 is rated at 15.20 SEER ARI cert # 1329596.
Both of them need TXV's etc...........I just did the quickest search
The blowers have to match. A G61MPV-60C-090 might use a different combo..........I did not check for that!
And if that second story unit is being installed horizontal in an attic, well that's a different coil again.
Hey Bob - Thank you for your help.
Is the TVX automatically included or do I need to make sure it is on the bid?
Bob is a Dave Lennox premier dealer, so he's the one to ask about your Lennox equipment. However, from his response, I got the inclination from his response that you needed the TXV separately. The C33 from the factory has an orifice metering device, and the TXV is an option. The CX34 has a TXV factory installed. My info comes from Lennox's engineering data for both coils. So it looks like either coil could be made to work. What did the contractor who quoted the C33 say about the TXV?
Yea anything with x in the mod.# is 410a on lennox and has to have a txv.