Do you ever work on your own stuff at home?? well I don't that often haha! I gotta say I have limited experience with Residential A/C. My system here at my place I don't think is doing that good of a job at cooling the place here, Yesterday it wouldn't even drop below 80*F where the stat is located, even with the temp outside yesterday around 85F and a bit of sun on 3 bigger windows with blinds closed it couldn't keep up. zoning issue maybe?
I'm going to pass on some info and we'll see what you guys think about this contraption!
Unit: Carrier M#38CK01834 (1.5ton??)
Coil: Custom Coils Inc. M#SA6979 (btu's ??)
Air handler: Temp Mizer High Velocity M# HV-52H 650CFM
Metering Device: Inline Orface
Measured at Condensing Unit
Suction: 67psi @ 42F(low superheat?)
Liquid: 210psi @ 97F
Condenser Air: 84F in, 95F out
Evap Air: 78F return, 61F Supply
Bristol pump M#H29B16UABCA OC 25
241V at contactor, 5.3A(@67psi suction)