after all this reading , put a negative vote to the plus side
proud owner of DV-22N.
To Keeping up with all this reading , coffe , Diet Dr Pepper, Green Tea.
"Accountability" is the key word here for those that don't "do the right thing" for our trade .
So now im ready not to be a "hack" according to you'll.
Matt 7:12 The Golden Rule
"Do for others what you would like them to do for you. This summary of all is taught in the law and the prophets.
My last job used to send me out to do startups and usually braze in the outdoor unit. Being a 2nd year at the time, I didn't have a ton of tools. So the first one they send me on the forman gives me the address and says " head out there, the installers are finishing up. They will have all the tools you need in order to get the unit running today." I get there to find out the outdoor unit has to be brazed in so I start on it, get all the pieces measured and what not. I'm just about to start brazing and I realize I almost forgot to use nitrogen. So I go get my gauges and go ask the installers where the notrogen is. In return, I get blank stares and ridicule. I think "wow, okay so apparently nitrogen maybe isn't that important for brazing, but how do you pressure test?" Feeling a little uncomfortable about the quality of the install I just figure I'll carry on and see what the boss thinks about this. The unit is now brazed in and since I have no nitrogen, I hook up my vacuum pump. Go to ask the other guys for a micron gauge, again blank stares, ridicule. I ask the guys how they can be sure about the integrity of the ststem when you haven't pressure tested, and you're not even checking with a micron gauge. They just kind of gave me puzzled stares like "who's this new know it all apprentice?"
End of the day, I go back to the shop and ask the foreman about these procedures, he laughs and says " I've been doing this for 25 years and I never use that stuff" I am in disbelief. The next day I go pick up some nitrogen and order micron gauges for me and another tech. I worked there for almost 1 year and couldn't believe how many installs that were less then 3 years old had service calls where the cause was low refrigerant. Hmmm I just don't understand why? Talk about a frustrating place to work- a second year apprentice going around fixing journeyman hack mistakes on a regular basis. An embarassing company to work for- my only regret is that it took me a year to get the brains to get the hell out of there.
if i still have contaminates in a system, how does that affect my reading on a micron gage? will my reading go higher (more microns) and how will i know it doesn't just have a leak?
Generally, if you blank off the vacuum pump at 500 microns and the system reading rises to about 1500 microns and stays there, you are boiling off more moisture. But if the reading keeps rising, you have a leak.
I think the poll show's that these forum's are doing what they are supposed to do. Helping tech's who want to learn with discussion's on what tools to use, when to use it, why to use it, and how to use it. Most of us here are further educate ourself's and mabie help someone else along the way so they don't make the same mistakes we did. The poll result's don't reflect what we see in the field generally.
Lots of things we weren't taught in school, such as a using a micron guage, reading static pressure, checking cfm's, and the list goes on. Doesn't make anyone a hack, just someone in need of more education.
It was here I learned I needed the YJ micron guage I now own and use instead of just pulling a triple vac. The same can be said for my Testo 605 H-2, 510, 410, and more to come. Don't know about everyone else, but I plan on keeping on learning untill I'm planted in the ground. Thanks to you guy's, the industry as a whole is improving all the time.
yeah when doing the practices talked/taught on here and seeing other peoples faces that are watching.....it kinda makes me think we split atoms or something with A/C and I'm about as green a noob as they come.......I can only imagine what some of the others are like with more exp. than I have years alive......you guys must have golden light emitting from your skin