One system or two?
Hi. In the market for a new system or two and hoping that you can help settle a discussion between my wife and I.
Our current system consists of two 10 SEER gibson units about 10 years old. Downstairs unit is 2 tons and upstairs is 2.5 tons. The downstairs unit has worked fine for the year that we have lived in the house. The upstairs unit recently developed it's second siginificant freon leak in the condensing unit. We are going to replace with a new R-410a unit rated at SEER 15 or better. Additionally, we have had two load calcs done with the same conclusion - our current units are not even close to the correct size. The load calcs suggest a 3.5 ton unit downstairs and only a 1.5 ton unit upstairs
Would you recommend replacing both units at the same time? What are the key factors we should consider in making the decision to replace the downstairs unit?
If you have an open floor plan do not believe the second floor calc. Do you reach setpoint easily on the second floor when it is really hot?
Originally Posted by MRT
Aire Serv of SW Connecticut- Gas heat, dual fuel and central a/c systems installed and serviced
Go with a single 15-17 SEER 2-speed unit with zoning. This will hit the best ROI sweet spot. You'll have only 1 unit to purchase, install and service. Be sure your lineset is replaced if there's any shadow of a doubt for needing to. Plan to splurge on a new Zero leakage R8 duct system with zoning.
Yes, it is an open floor plan, the upstairs is actually a loft open to the downstairs. The current system seems maintain the set temp. I think our current system was a DYI special, so it's more about thinking our current system is not designed properly. I think the calcs are probably correct.
Does the single unit with zoning esentially replicate having two units?
Thanks for the feedback.
Something seems wrong with the load calcs.
You have a 2 ton for the first floor that cools it fine, but the calc says its 1.5 tons too small.
Seems the current 2 ton is proving that calc incorrect.
So I would question the calc for the second floor also.
How long did they say it will take to redo your first floor duct work to handle the extra 600CFM of air that the 3.5 ton will need.
Open floor plans tend to let the warmer air of the first floor rise to the second floor, and the cooler air of the second floor drop to the first. I don't thing your calcs have taken any of this into account.
Since your ductwork is already set up for 2 systems, its not cost effective to have all the extra ductwork done to zone it.
Once the dutwork cost, and zoning controls and dampers are added in, may cost more then 2 systems.
Plus, if you only have one system, if it breaks down, your whole house is effected until they come out to fix it.
With 2 systems, one part of the house is still conditioned if one unit breaks down.
Plus, smaller units tend to be closer to their rated efficiency then larger units.
Some 4 and 5 ton up to 19 SEER units are closer to 15 then to 19.
If you go with these load calculation's, your wife is going to whup you. If it's maintaining now it doesn't need to be bigger.
Stick with two systems. Beenthere explained the reasons well.