Results 1 to 2 of 2
06-19-2008, 04:07 PM #1Regular Guest
- Join Date
- Jun 2008
Question about York Affinity PV9 series
Just got a new York 94% efficiency furnace with variable speed ECM motor. When the blower motor starts, it makes a bumping noise / vibration for about 5 seconds, rattling the ducts even. York contractor says all ECM motors do this on start. Can anyone experienced with these motors tell me if it is normal? Many thanks...
06-19-2008, 05:47 PM #2
The ECM is checking its self for correct rotation. Its common for all ECM blowers to do it.
If your ductwork is metal, he should have used a flex connector to isolate the furnace/AC coil from the duct.Contractor locator map
How many times must one fix something before it is fixed?