10 ton system with 4 distributor tubes - I find it is odd ? Did not say it is wrong
Circuit #1 and #2 -- are they tied together as one common suction line out of the coil ?
30 PSIG and 16 degree suction line temp -- that gives you 9 degrees super heat and not at NO SUPER HEAT
I can get the sporlyn part number on the distributor.
my TP chart at the time i measured this units superheat was zero. i am not looking at a chart now but i think 30psi R22 = 16-18 degrees F
This unit has two compressor circuits and condenser circuits no common piping. i would like to clear my confusion and understand what can cause this symptom.