Hello, I installed a 1.5 ton Tane Heatpump for the second floor of a 2 zone system. After starting the system up I noticed the suction pressure was running around 100 psi and the head pressure was around 215 psi. it is an R 22 system. The outside air temp was 95 degrees and the inside temp was 85 degrees when I started the system up. I am getting around a 67 degree discharge and the suction line is sweating back to the compressor. I'm not sure what is causing the suction pressure to run that high. I was thinking maybe the TXV valve was not working correctly. Doeas anyone have any Suggestions?