My heat pump went out and can't be repaired reasonably.
I had a load calc done, and found out that the original was about a half ton shy of what it should be and that a return should have been installed on the lower floor.
I actually went through the numbers with the technician and he was correct.
The company is recommending at the base level a new Goodman 2.5 ton at 14 SEER. I would like to step it up a little and get the 16 SEER. He says he will investigate my options.
As best I can tell, Goodman doesn't make a 2.5 ton 16 SEER unit is this correct?
Should I stick with the 14 or step up to a 3 ton 16SEER. Also, is a VS unit available, and a 2 speed pump?
I appreciate your recommendations and advice!