I always miss the great ones.
Off Dove Rd.
Get there call not cooling, first blown fan run capacitor, replaced 7.5uF and ck, amps , bearings ok. Then low refrigerant, but, wait this is a Friedrich 1972 model system with original coil, updated York furnace.D-Tek and open coil, oily and leaking both sides cap-tubes and tube sheets. Well, lets find out what we need to do to get a new coil, remove furnace, upper/lower combustion,gas lines mastic,drains, breaker 60amp on condenser, and in large R.A.G.<<<>>>.
Give him an estimate for repairs and AHS will replace coil, but he should replace condenser also, nope just coil.. Man how cheap can some people be.
He could save about 800.00+ a year with just spending a little money to upgrade 1972 >7.0 EER condenser.