I have airhandler with xl-50 was working fine until the other day when I had steam valve actuator fail and went off on high supply temp. Changed actuator, cleared alarms, now I dont know how to restart application. Shows application stopped but mode is occupied so fans etc should run. Unit operates normally in manual modes for DO and AO points (fans,valves,etc). I have no prior experience with these controllers, any help appreciated.