hi. i have a new goodman heat pump. it has an annoying problem since day one. it worked fine all winter except for this noise problem.
When it goes into
defrost the compressor gets very loud for about 10 seconds. it sounds
like it might blow up. It sounds like its digesting raw refrigerant. I
fear its going to ruin the compressor.
I have had it checked twice by techs but they can't find anything wrong. it is a
3.5 ton Goodman 14 seer heat pump system GSH130421A/AEPF42601A
i contacted goodman and here is what they said. does this sound like it could be the problem. has anyone had a similar experience? before i have a serviceman out another time i would like some opinions. i live in a rural area and techs here dont seem that knowledgable about heat pumps. here is what goodman said:
Thank you for contacting GoodmanMfg Co.
We sincerely regret any difficulties you have experienced with our
Out tech support department has informed me that the technician should
be checking for a slow moving reversing valve. He is welcome to contact
us while he is the unit for assistance with resolving any issues with