Results 1 to 3 of 3
Thread: Lennox Heat Pump
03-26-2008, 10:48 AM #1
Lennox Heat Pump
I went to a house the other day for a no heat call. I found the reversing valve to be stuck in cooling mode when the coil is de-energized. The unit is 7 years old and has had 3 RV coils replaced ( one of them 3 weeks ago ). The pressures were great for cooling mode. So I diagnose that the RV is no good. I returned the next day to install the reversing valve and when I removed the old one I find a 3/8" street 90 in the center 7/8" copper stub coming out of the valve. I turned the valve up side down and it fell out all dented and beat up. I was wondering if any one has seen this sort of thing before.
03-26-2008, 01:53 PM #2
I never have.
Must of been a disgruntled guy on the line the day that one was assembled.Contractor locator map
How many times must one fix something before it is fixed?
03-26-2008, 02:39 PM #3Professional Member*
- Join Date
- Dec 2005
The coil and the valve are not match then. It buzzed so they did that.