Anyone having issues with this board in an ICP furnace??
Fan NOT coming on after 30-60 secs on a call for heat.....
(blower does come on after 2 mins by main limit opening)
Replaced the board, and even with the new one, still no 115 to neutral & heat tap! WTF?!
Can't be a bad board (heat fan relay) out of the box, can it??
Played w/ the dip switch settings... no blower, until limit opens.. Grrrrrrr!
T-stat wires are off the board, Just R & W jumped out..
I'm just going to put in a separate time delay relay & wire it up to the blower on a call for heat either 24v C+W or make & break continuity R+W, but still WTF?!!!!!!!
Dare I try another board?????????????