Service techs test systems, how many of you tell design and sales 6 inch flex duct does not move 100cfm. I fight this constantly. RNC design says 16 6" runs move 1600 cfm. My static is .89 IWC. 4 ton system, 14 inch trunkline. The big problem, installers own the company and they believe the old adage"industry standard"