# Thread: Cooling tower water consumption per ton of refrigeration

1. Regular Guest
Join Date
Jul 2007
Posts
23
Post Likes

## Cooling tower water consumption per ton of refrigeration

Hi all,

How much water is expected to be consumed by a cooling tower per ton of refrigeration?

From the wikipedia article:
A ton of air-conditioning is the rejection of 12,000 Btu/hour (12,661 kJ/hour). The equivalent ton on the cooling tower side actually rejects about 15,000 Btu/hour (15,826 kJ/hour) due to the heat-equivalent of the energy needed to drive the chiller's compressor. This equivalent ton is defined as the heat rejection in cooling 3 U.S. gallons/minute (1,500 pound/hour) of water 10&#176;F, which amounts to 15,000 Btu/hour, or a chiller coefficient-of-performance (COP) of 4.0 (or EER of 13.65).
At first I misread the article as saying 15,000 Btu/hour would evaporate 3 gallons per minute. It is actually saying that 15,000 Btu/hour equals delta T of 10F at 3 gallons per minute.

To estimate evaporation rate needed to reject heat for per ton of refrigeration, I would do:
(15000 btu per hour) / (2260 kJ/litre) = 0.030 US gallons per minute
or 0.1167 litres per minute
or 0.168 m^3 per day

since 15000 Btu/hour is the heat dumped out by a chiller of COP:4.
and since 2260 kJ/litre is the heat of vaporization of water
and since I assume that all the heat rejection is due to evaporation... this is a big assumption, since cooling tower exhaust air is at higher temperature than inlet too.

2. Regular Guest
Join Date
May 2007
Posts
82
Post Likes
I've never seen the formula you're using. The one I've used in the past is:

Evaporation Loss = 0.00085 * water flowrate(T1-T2)

flow in GPM and T in F. Some use 0.001 instead of 0.00085 it just depends on how close you want to get. Basically, evaporation works out to about 1% (or 0.85%) of the flowrate for every 10 degree temp change.

3. There are 3 components that determine cooling tower make-up:

d
• rift loss due to the wind
• evaporation due to the heat transfer process
• blowdown required to keep maintain an acceptable level of TDS (total disolved solids)

You can go to just about any cooling tower mfrs website to get more info & understand the calc. You'll end up seeing that blowdown is the largest contributor to make-up water flow rate. A rule of thumb is about 1% of the condenser water flow rate, assuming a 10 deg Delta T, of course it depends of the quantity of TDS in the make-up water. If you have well water, you'll use more if you have city water & treat it w/ a softener you'll use less.

4. The rule of thumb was 3 Gallons per ton per minute MAX for sizing water makeup for cooling towers.

#### Posting Permissions

• You may not post new threads
• You may not post replies
• You may not post attachments
• You may not edit your posts
•

## Related Forums

The place where Electrical professionals meet.