im setting up a e2 and have put 5vc 200# tranducers on the oil pumps....went into compressor output set up and chose pressure switch for oil...set my delay for 10 seconds (it was default), set my net for 15 psi....ive also set this for auto reset, its supposed to wait 10 minutes before a retry, then as luck would have it i have a 6hp thats LRA, so i am able to test this set up.....but it works odd....it tries to run (conactor pulled in, but ive shut the breaker off).....10 seconds later the e2 shows an alarm...but it keeps the control circuit energized....exactly 10 minutes later it goes into the lockout mode where i have to clear the alarm....although i will have the 9# manual resets on the machine, im a little concerned about the reliabilty of this, the manual dont really cover oil, the on screen help is sketchy to me, and the telemarketers answering the phones havent been able to provide much help
id hate to think i had zero oil pressure for 10 minutes if i were relying soley on the e2...im sure i have not got something assigned in either an input or an output.....any help? 2 suction groups by the way if it makes a diff..
btw, i would also love to see either pump pressure or net pressure on the suction group user screen or somewhere easy, but not sure f thats possible either....i can go into board inputs and see pump pressure when a compressor is running....
also, if i unplug the sensor, it still says "good" on the suction group screen