Has anyone else gotten calls from their customers complaining that the AC didn't turn on this morning (Jan 2nd)? All of mine did. Or at least they would have if I wasn't near an internet connection to restore the iLON schedules. Basically what happened is that after the New Years Holiday, all of my iLON schedules were locked out. I first checked the web pages and the configurations looked fine but the schedule outputs were in the off mode. After I manually overode the outputs to get the equipment back up, I launched LonMaker and opened the plug-in. Each schedule had the start and stop date enable box unchecked. However, when I looked at the web page schedule configuration they were checked. For some reason (bug, feature, or user error?) the schedule start and stop date enable didn't match what I saw on the web page compared to what I saw in the plug-in. After checking the boxes in the plug-in everything went back to normal. I also tried unchecking and rechecking the boxes in the web page and that worked too. I just talked to Echelon support and no one else has reported this issue. I suppose it could be an error related to my programming of holiday schedules. Anyway I would like to know if this is in fact a scheduling issue with the iLON or do I need to read the holiday scheduling chapter in the user-guide.