Results 14 to 16 of 16
Thread: gravity fed walk in cooler
12-08-2011, 09:52 AM #14
The nature of gravity coils....no air movement in the box....can easily result in what you are describing. The moment someone enters the box, the temperature will increase. With no air movement it takes a long time for the heat transfer process between the air and refrigerant, and depending on gravity to circulate the air and get even air temperature takes a long time too.
Unless the thermostat is mounted substantially above the product level it's hard to understand why the product is freezing...unless the stat isn't accurate.
It would be interesting to check the temperature at different heights....say, after a defrost period....to see how much variation there is between where the product is located and where the stat is located.
What is the product they are refrigerating and how often are they in/out of the box?
Good idea to add the head pressure control valve in a climate like Colorado. I'm with the suggestion to replace the gravity coil with a tradiional fan/coil unit. There's a reason why you rarely see a gravity coil in a walk-in box.
12-08-2011, 08:21 PM #15Regular Guest
- Join Date
- Sep 2011
- Plainfield IL
I think your problem might be with the freon choice. Off time is very important for controlling your icing. Running MP39 means less off cycles which means more ice. If the customer would let you, you may want to suggest converting back to R-12.
My personal R-12 repalcement gas preference is hot-shot but not sure if its more efficient than MP39 though.
12-08-2011, 08:37 PM #16