Inducer motor fills with water
Hi there. Our new Goodman furnace frequently does not start up. Removed name of company and owner installed our furnace and assured us that he had installed it correctly. They later installed a drain on the exhaust pipe to help to drain the furnace, but that didn't help either. Can anyone here that is familiar with goodman comment on their "fix" for the flooding inducer motor?
Below is a photo of the installation:
Last edited by HeyBob; 07-15-2008 at 09:02 AM.
Reason: See above