To be considered BACnet compliant, is there a list that states what points have to be shown per unit?
Does the standard just state that if you have a analog output that you must provide these points. Or does it state that if you have a AHU or RTU that you provide setpoints, inputs, outputs etc..
Specifically i have a contractor that states they will not provide setpoints for RTUs and VAVs because the standard does not state they have to. They will only provide status of the points, ie Supply Air Temp, %cool, %heat, etc..
So does the BACnet standard state they have to specifically allow setpoints to be seen and adjusted?