A new Goodman heat pump (GSH14) with a ARUF 374316 air handler seem to putout more cold air then the old Goodman system when the blower comes on.
Tear out that POS and start over.
We missed you at the last convention, it was discussed in great detail, too bad.
Hey cockroach, don't bug me! ©
Bring Em Home....
Can someone move this thread to the Residential Forum?
Aircraft Mechanical Accessories Technician. The Air Force changed the job title to Air Craft Environmental Systems Technician. But I've decided I'll always be a Mech Acc.
I apparently posted this on the wrong site
FYI I am a tech on refrigerated compressed air dryers and do not normally deal with home HVAC
I have the exact same heat pump and air handler.
Last night, it was 28 degrees outside. I measured 90.1 degrees directly after the coil in the air handler after the system had run for an hour. The heat pump had not gone into defrost yet.
The Expanded Heating Data in Goodman's Product Specs calls for a 23.4 delta T when it is 30 degrees outside.
There is a Time Delay Relay of 7 seconds from the start of the compressor to the start of the blower fan.
I would be interested in hearing about the discussion on this topic.