Here is a photo of the old coil in the system.
and the new one that the "pro" replace it
Twilli says get a Coleman stove.
No Heat No Cool You need Action Fast
twilli has good advice
I dont warranty Tinkeritus
Originally Posted by orlandotech
I thought that was a BS thread to get Robo, Carnak and Made to start fighting again like the old days.
Is that thing still broke? WTF??!!
gotta be the Board, or the draft switch ..
problem floats around ..
onetime, it don't open the gv, next time blower starts before id fan, id fan cycles like crazy, then it goes away ...
thank god it's not a customers furnace
i don't want to work on my own furnace ..
the job pays nothing ..
can't you guys tell me whats wrong over the internet ..??
slim i just hacked into your circuit board on your goodman and i get a code 34.
you need to pay your utility bill.
Something like that happened to one of our install jobs one time and they ended up having me install a larger pump on the system. They said something about feethead of the pump wasnt enough for the new coil.