A tripped oil safety switch doesn't necessarily indicate a flood back problem. A single phase condition, caused by either a power failure, or burned contacts on the compressor contactors could also cause your oss to trip. I suspect this was a gradual condition, ocuring over several days. if the system is computer driven, you may be able to access the history logs to help you determine what happened.
remember, no good deed goes unpunished