1. Regular Guest
Join Date
Nov 2007
Posts
71
Post Likes

## Correct btu?

I know a lot goes into furnace sizing. That said, I'm replacing a 17yr old,
100,000 btu Bryant. It's probably 70% - 75% efficient. My home is two floors, about 2,400 sqft. I live in Cincinnati, OH and we can get some pretty cold stretches. I'm putting in a Rheem 90% + modulating and have two reputable quotes. On says a 90,000 btu will do just fine. The other says a 90,000 is 'maybe just enough' and suggests going to the next step, a 105,000btu. Any suggestions?

2. A 100,000 btu at 70&#37; means a 70,000 btu output.

A 90,000 btu Rheem has 86,000 btu output.

A 75,000 btu Rheem has 72,000 btu output.

The 75,000 btu Rheem will put out more heat than your current furnace.

3. Professional Member
Join Date
Sep 2002
Location
South Dakota
Posts
6,580
Post Likes
A furnace as old as yours is far less than 70% efficient. More like 50 to 60% efficient.

4. Did anyone perform heat loss calcs?

5. amd
Regular Member
Join Date
Sep 2002
Location
I don't know
Posts
3,022
Post Likes
Originally Posted by NormChris
A furnace as old as yours is far less than 70&#37; efficient. More like 50 to 60% efficient.
80% efficient units with inducers existed 17 years ago. So did natural draft furnaces with dampers and electronic ignition. (65-70% seasonal, 75-80% steady state)

6. Regular Guest
Join Date
Apr 2005
Location
CT
Posts
25
Post Likes
Make them perform a heat loss calculation, that is the only way to know if the furnace that you are getting is the rigth one. If they dont perfom a load calculation they are guessing and you going to have an oversize or undersize furnace.

I hope this help.

Hernan

7. First, the boys saying LOAD CALC are the only ones making sense!

Second, AFUE doesn't always tell what the output is. You may have a unit with AFUE of 60% but in steady state operation, the output is around 80% of the input. Look at the rating plate! So just because he has an older 100K furnace, doesn't mean the output is any less than 80K.

You can take a 50s vintage relic and once it is warmed up, the house is getting 80% of the heat the beast is making. But it is still likely wasting 40-50% of the heat you pay for. Why? Because AFUE looks at all losses and oldies lost a lot of heat up the flue as they warmed up and as they cooled down. The more oversized and the more cycling, they more they lost. But once at temp, they weren't too bad. So below 80% AFUE, pretty much figure output at 80% anyway.

Just on the guess aspect, 2400 sq ft decently built house in Cincy, 90K max. But as the wise men before me have said, only a load calc will tell for sure.

8. Regular Guest
Join Date
Nov 2007
Posts
71
Post Likes
Thanks, all. My old Bryant was pretty much their basic at the time. Never any problems with it, but I'm sure it's efficiency is low. In any event, I'll make sure to have the load calc done. Thanks again!

#### Posting Permissions

• You may not post new threads
• You may not post replies
• You may not post attachments
• You may not edit your posts
•

## Related Forums

The place where Electrical professionals meet.