Them thar newmatics...
Use 1 pilot signal with the bypass valve positioner set up to close at 50% of span, then the pressure switches for the fans staged on the top 50% of the pilot span.
Or use separate signals for the bypass and the fan staging.
God Bless our Veterans
God Bless the USA