I got a 7.5 ton split system with hot water coil. It feeds a big lobby. It just dumps into it. They have built a small office off the side. There is a 8 in line that comes of the lobby unit. Would a bypass application work for this. Do you think I will have freezing issues when bypassing all the air except the one 8 in line?