Originally Posted by chandleraz_guy
Tech claimed pressures were good with disch press=220, suct=76, superheat=8, sub-cool=13, and ambient=89f.
The system may be overcharged, depending on the length and lift of the refrigerant lines.
Last edited by mark beiser; 10-27-2007 at 12:02 AM.
If more government is the answer, then it's a really stupid question.