Has anyone used the above control on a furnace blower and or conderser fan motor.....where you impressed, or did it not make a difference. Love some of your inputs
Need to use a ball bearing motor too.Don't see where it's worth the money.
I had one in my package heat pump, kind of unrefined but it did work.
I had good luck using the G.E. motor that came with the unit, although some motors will apparently make racket with it.
I took it out of the unit a couple months back and will probably get rid of it.
I use them on some condensers, for low ambient operation.
Set up right. you can use a sleeve bearing motor.
Set wrong, the sleeve bearing motor dies quickly.
Contractor locator map
How many times must one fix something before it is fixed?