Are the uc400 and uc600 considered full load devices?
Beware of the prophet trying to make a profit.
There is less oxygen from knee level to the floor! Check it out next time you tie your boots.
he is asking about rs485 loading I assume. Only Trane can tell you what type of rs485 transceiver they have used.
Yes I have acquired a network that potentially could have 75 uc400 and uc600s and over 5000 ft. Trying to talk them into splitting the network and not the band aid of repeaters.
Here is the UC400 paperwork from Trane.
I know to split it, trying to give the rock hard facts and not just "best practice" if they are anything more than half load devices it won't work.
More than 60 and you will have problems. Also id watch going over 4000 ft.
Last edited by scrooloose; 09-05-2013 at 10:34 PM.
That is exactly what I was looking for preciate it!