I went out on a york 4 ton package heat pump, call was a no cool.p.s.i. was 110/225 out door temp. was 104 . condenser motor is bad. suction line temp. at comp. was 77. unit has the dryer in the discharge line before the reversing valve from factory. scroll comp. Change out compressor?