I am working on a Trane air handler (240V) connected to a 150 ton Trane chiller. This equipment has been wired to a computer interface for laptop access to turn on/off, scheduling, ETC. When powered up The blower kicks on and the A-coil gets to approx.56 degrees on the inlet and condesates well, but the forced air to the registers only gets to 76 degrees. Filters are clean and I cant seem to fix it where I get nice cold air through the registers. Anyone had this issue before?