looks ok to me also
We really need change now
Originally Posted by just_opinion
That does not look bad. There is a lot of heat load at 82 DB and 72 WB.
I hate when a tech give me 95 PSIG. I prefer we all use SST at 56 degrees. And SCT at 110
This way we don't have to ask "what freon is it?" and go get a P/T chart.
Don't we all agrees.
Yea i like that idea leads to less confusion
I lost the model and serial number and i was down the street so i stoped by to write them down and they said it was working pretty good... Didnt have any gages or thermometers to check any thing
It can take a good 15 to 20 minutes for the condenser to dry after you hose it down and clean the coil.
Contractor locator map
How many times must one fix something before it is fixed?