Lets just say that you are a tech and the problem is a short in your t-stat wire. You should know how to at least narrow down to the wire with the short. If you cant find the kink with in arms length of the furnace then I would replace the whole run. It works for me everytime I have a short in the low- voltage wire.
If your not getting the results you desire then change. People change from either desperation or inspiration.
Regardless of your disagreement with the site rules, this site does not exist to provide DIY assistance. Therefore, your post was removed. The OP may in fact be a professional in the trade. However, troubleshooting posts are not permitted in the open forums.
This is at least the second time a moderator has removed one of your posts.
Your posting privileges have been removed for one week.
Last edited by jrbenny; 05-09-2007 at 12:01 AM.
Perhaps you should have read the instructions before calling.