I have just received manuals to the 30T chiller
but a distributor-tech 3way call , when discussed, said the limit was for the equipment - and always "on"
common sense cert in hand, I question this.
this programmable intellipak is shutting off and interim nights of long - low loading swings ,
when it is above 80 ambient; chiller in standby, then it trips and goes to warning light... finding the next morning
; internal "hot-start" limit setting max's to an 80 deg set point as I roll through the configs and sets...
building owners who handed me my CS CERT at lunch last week ONE DAY BEFORE THE TRIP
said "that's al we expect: CS"
- agreeing to their terms, I picked up and am the proud holder of a CS certificate
any internal setpoint config pages to read out of the 8 manuals I just grabbed.