Thanks for all the help guys. After reading all of your input and doing what you guys said, I removed almost 3 lbs of 22 from the system. I think the lack of return and the guy doing the original setup using "rule" of thumb to compensate for the low evap temp is what caused the issue. I charged according to the superheat chart to 20*. I was reading 0 before. Now the compressor starts perfect and quiet and system runs excellent.