Hello hvac pros, I recently had a new system installed and well on my contract I was supposed to get a 16 seer unit and while the condenser is 16 seer the coil that was put in is a 3rd party ADP coil that lowers my seer down to 14.5 with a 12 EER rating. My question is if my contract states 16 seer on it should I have expected 16 or is this normal practice? My system info is down below. Thanks for any input comments and suggestions all are welcome. P.S. I haven't talked the contractor yet I wanted to get your guys opinion first if I was to talk to him about this.
Outdoor unit: 24ACC648A003 4 ton carrier performance
Indoor unit: C60A210C166 ADP coil
Furnace: 59SP5A100E21--20 Performance Series Boost
AHRI nr: 5372769