Have a trane 410A High eff. Cond, & Furnace, Cond md # 4TTX5036A1000AA, Didn't get the furnace and coil numbers today.............
Any ways, I'm getting stumped a bit,
O/A 98 deg.
hp 485, liquid temp 100
sp 125 suction temp 70
air across coil rtrn 79 supply 67
clean filter, cleaned cond, coil.
pulled charge and recharged with new liquid 410A. after I saw hp of 510 with 95 deg liquid.
Comp rated 15.4 a/ 14.8
Cond fan looks to be running high speed, didnp[t get into electronic today,
Problem I feel is txv ???? Best super heat is 26-28 deg.
adding freon raises hp, sp but does little to lower suction temp.
Going back tomarrow,
Pondering >>>>> is the txv holding open, unit froozed past weekend, filter was trashed bad, so I'm thinkin that caused the freeeze, with good air, why is the suction so warm, and the head so high ????
Not much time under belt for this 410A stuff, added with the energy unit on top. I know I will need to get to the electronics and confirm speeds for the fans..............
Indoor coil I rmember as the proper size for the cond, 3 ton >>..