Ok guys finally got back to customers and replaced board. I lost the "heat" call to the blower, great.Walked outside to write up bill,condenser is running!Go inside blowers off! WTF! I did not mention in my original post,"intermitant water under furnace". Found call for cool at Y,not at G. Replaced thermostate (explain that to customer!) problem solved,I hope!