Anyone have experience with LG's version of the VRF systems? Looking for input on the LON or BACnet interface. Manual is not very clear.
"Fortunately, I keep my feathers numbered for just such an emergency." Foghorn Leghorn
What do you want to know?
Does it work? Does one work better than the other for the interface? Will control of set points and scheduling be available or is it more of a monitor only interface?
They work. I would take the BACnet over Lon. More functionality, more capacity, and less issues. They are both monitoring and control. You can see the points lists here:
Thanks El Presidente!
You're welcome! Let me know if you need anything else.
Something good to know about the BACnet gateway though is that certain SW versions only work with certain BACnet manufacturers. ie Delta works with 1.30.x, Reliable with 2.00.1d
Follow me @blankscole